Flexible busbars for transformers with a capacity of 1000 kVA
Flexible busbars are intended for use in low voltage chambers of flameproof transformers manufactured by AEG “MEFTA” (GEC Alsthom) – Mikołów with a power of 1000 kVA.
Flexible busbars are used to make connections between the bushings providing voltage from the flameproof tank of flameproof transformers manufactured by AEG “MEFTA” (GEC Alsthom) – Mikołów of the transformer core, and the lower terminals of the SH-630 / M circuit breaker.
Flexible busbars are made of a single conductor 95mm2 with rubber insulation made of flame-retardant rubber.
- The ends of the flexible rails are pressed in copper sleeves.
- Mounting holes are drilled in the pressed ends of the rail (clamp).
- The pressed ends of the rails are galvanized with zinc.
Technical data of flexible busbars for 1000 kVA transformers
|Drain rated current In||275 A|
|Rail cross-section||1×95 mm2|
|End clamp dimensions||38x38x13 mm|
|Mounting holes diameter||Ø17,5 mm|
|Outflow II Q2||Outflow II Q3|
|Lp||Length||Number of fasteners per set||Lp||Length||Number of fasteners per set|
|1||1080 mm||1 szt.||1||720 mm||1 piece|
|2||1120 mm||1 szt.||2||820 mm||1 piece|
|3||1160 mm||1 szt.||3||1000 mm||1 piece|
Download the catalog card: